This section will show photos of horn, horn/strobe, and strobe installations.
The next photo may show a horn/strobe installed with writing not orientated correctly:
The next photo will show a horn/strobe detached from its base. Subsequent photos will show the horn/strobe to be substantially damaged:
The next three (3) photos will show additional views of the above referenced horn/strobe. Note the apparent damage:
The next two (2) photos show the above horn/strobe removed from service:
The next two (2) photos may show a partially obstructed horn/strobe:
The next photo may show a horn/strobe installed in a gym with a protective cover that is partially detached:
The following photo may show a horn/strobe partially detached from structure:
The next photo may show a horn/strobe detached from structure:
The next photo may show a client/owner painted horn/strobe:
Below, a photograph shows a horn subjected to extreme cold environment:
The photo below may shown horn/strobe not installed at the correct height"
Below, a photograph may show an incorrectly installed horn/strobe. Also note, the conduit may be disconnected from the backbox.
Another view showing the conduit discussed above:
Another view of the same install:
The picture below will show what may be heavy chains and other external loads on the above noted horn/strobe conduit. This may be a contributing factor in the conduit separation/disconnection: