The following series of photos shows "Vic" type couplings (and a "744" type adapter) that have moved out of their "groove", likely a result of hydraulic shock. The couplings were on piping located within a pump house. The pump suffered mechanical failure.
The degree of movement is indicated by the tape measure:
Another coupling mechanical failure:
Here's another photo of the same coupling: