This control valve is missing tamper protection, signage AND the control valve partially obstructs access to stairs (located to the left in the photo). The valve may or may not be listed for fire protection service.
From another angle:
Below, a photograph shows an OS&Y control valve with a packing leak. No signage is shown.
A close up:
The photo below shows an OS&Y control valve on a fire line that until recently was not supervised:
When was this butterfly valve last exercised? Does the tamper work? Kuwait City.
Tamper Protection and Signs missing from this control valve. Parking garage, Kuwait City, April 2017:
Tamper Protection? When was this valve last turned?